LC LITEAIR Condensing Unit Location
The Hubbard LITEAIR LC unit can either be mounted on a level surface or suspended from a vertical wall.
The unit should always be mounted on a load bearing wall and NOT a partition wall.
The sides should have a minimum clearance from obstruction of 600mm and the minimum clearance for the front of the machine should be 1.0 metres. The minimum clearance for the rear of the machine should be 130mm.
Two-off hole fixings and two-off slot fixings suitable for M10 fixings are provided in the base of the unit to secure the unit to a suitable plinth, or to wall mount brackets. If required, the contractor should install the unit on anti-vibration pads.
The refrigerant pipe and electrical connections are located at the right hand end of the unit. Ensure there is adequate air entry at the back of the unit.
NB ENSURE THE CONDENSER HAS ADEQUATE CLEARANCE AROUND IT AND IS NOT AFFECTED BY NEIGHBOURING CONDENSING UNITS AND OTHER OBSTRUCTIONS.
LE LITEAIR Evaporator Unit Location
The Hubbard LITEAIR LE unit should be mounted level on a load bearing wall or ceiling. The minimum distance from the floor should be 1.8 metres to ensure good air convection.
The sides should have a minimum clearance from obstruction of 100mm and the minimum clearance for the front of the machine should be 1.5 metres.
The unit should be fixed to the wall using two-off rear fixings or to the ceiling using the two-off top fixings. 10mm Rawl Bolts with large steel washers are recommended for fixing to a local load bearing wall or ceiling. Locking screw holes to be used to prevent equipment moving once installed.
The refrigerant pipe connections are accessed through the left hand side panel.
Cable entry is on the right hand side of the unit. A plastic drain connector is supplied to be site fitted onto the condensate tray.
Technical helpline 01473 892280
We reserve the right to change specifications without notice. Details correct at time of going to press.Hubbard Products Ltd, Blue Stem Rd, Ipswich, IP3 9RR Tel: 01473 892289 Fax: 01473 892345
E-mail: firstname.lastname@example.org Web: www.hubbardproducts.com
To download the Installation Guide for this product Click Here